Arc flash programme delivered successfully while working with a multinational data centre engineering team. The programme has been implemented on multiple client sites in Europe. By building the facilities electrical network in an advanced power modeling software, Premium Power performed arc flash analysis using the IEEE 1584 calculation method and short circuit analysis in accordance with IEC
Being a US multi-national operating out of Europe, one of the main challenges was to achieve compliance with EU health and safety requirements as well as meet the demands of the client’s global corporate standard, which was heavily linked to US electrical standards. To calculate the magnitude/severity of a potential arc flash hazard it is critical that the correct information be used during the modelling exercise. The hi-tech data centre’s electrical network had over 400 electrical panels with the number of electrical components to be assessed and modelled exceeding 1000 bus.
By developing a co-op between Premium Power and the client’s engineering team, a full review of the electrical system was performed to validate the installed electrical equipment. Using SKM Power Tool software, Premium Power engineers simulated the electrical system before conducting extensive arc flash analysis. Arc flash analysis proved that there were a number of areas that required immediate action to mitigate against the high incident energy levels.
“This project highlights the importance of power system modelling. Without knowing the magnitude of the arc flash hazard, it would have been impossible to design it out and reduce the risk. The analysis led to the design of simple and cost effective control measures that could ultimately prevent serious injury or fatality to the electrical operators on site.”
By identifying the magnitude of the arc flash hazard, suitable arc flash mitigation was designed and applied to significantly reduce the severity of the potential hazard. While reviewing the site’s existing protection coordination for the purpose of arc flash mitigation, additional protection setting recommendations were made to enhance site reliability while achieving safer working conditions for electrical personnel.
Power Quality is more problematic than ever. This is increasingly the case as modern industrial and data centers use equipment that is both very sensitive to poor power quality and ...