POWER STUDIES FOR DATACENTRE GRID CONNECTION APPROVAL
Working directly with a global multinational data center client we were able to develop comprehensive power system models in order to ensure they were compliant with local TSO grid connection requirements.
of all Data Centres in Europe
of the states power requirements
Locations in Ireland
Our confidential data center client with a rapidly growing fleet of facilities was looking to connect a 70 MW facility to the 110-kV transmission system. We were asked to carry out power quality analysis (harmonics & transformer inrush) at the sites 220 kV PCC to ensure full compliance with the grid requirements. The project also includes power systems analysis (short circuit, protection coordination and arc flash analysis) within the client’s facility to ensure optimum reliability and safety in all fault conditions.
HOW WE HELPED
Premium Power developed comprehensive power systems models using two different software types, DIgSILENT (PQ analysis) and SKM (power systems analysis). The project was delivered in two stages.
- PQ analysis using DIgSILENT to identify VTHD at the 220 kV PCC. The PQ analysis was also used to assess the grid transformers/grids response during transformer start up.
- Power systems analysis; short circuit calculations were used to assist in the design of both MV & LV protection schemes. Following this prospective arc incident energies were calculated for all 3-phase equipment types.
The PQ analysis showed that the Client was 100% complaint with the requirements set out by the TSO (transmission system operator). This meant there were no delays in grid transformer energisation, which in turn meant the Client was on course to delivering power to the critical load on schedule.
The power systems analysis meant the protection schemes were designed to achieve a reliable, safe electrical system and the settings were designed to ensure prospective arc incident energies were minimised while achieving optimum grading on site.
The client wished to remain anonymous, however they were a multinational date centre with a 70 MW facility.
”"Premium Power consistently delivered a high quality service under extremely tight time constraints. Feedback from the utility company stated that the grid PQ compliance report was the best they had ever received."George MoklElectrical Engineer